Model: PD6001-7H2 Product Type: 1/8 DIN Feet & Inches Level Digital Panel Meter Input: Current (4-20 mA), Voltage (0-10 V) Output Options: 2 Relays Power: 12-24 VDC/VAC Approvals: CE, UL/C-UL Transmitter Power: 24 VDC @ 100 mA Display Category: LED, Dual Line, Sunlight Readable, Feet & Inches Display: SunBright, 0.6″, Dual Line, 6 Digits, F & I, Red LED Warranty: 3 years Product Series: ProVu Product Family: PD6001 Product category: Digital Panel Meters Product Application: Level, Process, Pump Control
Display: Upper feet & inches display: 0.60″ (15 mm) high with feet & inches designations. Lower display: 0.46″ (12 mm) high. Both are 6 digits (-99999 to 999999), red LEDs. Feet & Inches Display Range: 0″ 00″ 0/16″ to 99″ 11″ 15/16″ Display Intensity: Eight intensity levels Display Update Rate: 5/second (200 ms) Overrange: Display flashes 999999 Underrange: Display flashes -99999 Display Assignment: The upper and lower displays may be assigned to PV1, PV2, PCT (percent), max/min, alternate max & min, set points, units (lower display only), or Modbus input. Front Panel: NEMA 4X, IP65 Programming Methods: Four front panel buttons, digital inputs, PC and MeterView Pro software, Modbus registers F4 Digital Input Contacts: 3.3 VDC on contact. Connect normally open contacts across F4 to COM. F4 Digital Input Logic Levels: Logic High: 3 to 5 VDC Logic Low: 0 to 1.25 VDC Noise filter: Programmable from 2 to 199 (0 will disable filter) Filter Bypass: Programmable from 0.1 to 99.9% of calibrated span Recalibration: Calibrated at the factory. Recalibration is recommended at least every 12 months. Max/Min Display: Max / min readings reached by the process are stored until reset by the user or until power to the meter is turned off. Password: Three programmable passwords restrict modification of programmed settings. Non-Volatile Memory: All programmed settings are stored in nonvolatile memory for a minimum of ten years if power is lost. Input Power Options: 85-265 VAC 50/60 Hz, 90-265 VDC, 20 W max or 12-24 VDC ± 10%, 15 W max. Powered over USB for configuration only. Fuse: Required external fuse: UL Recognized, 5 A max, slow blow; up to 6 meters may share one 5 A fuse. Isolated Transmitter Power Supply: Terminals P+ & P-: 24 VDC ± 10%. 12-24 VDC powered skus selectable for 24, 10, or 5 VDC supply (internal P+/P- switch). 85-265 VAC skus rated @ 200 mA max, 12-24 VDC powered skus rated @ 100 mA max, @ 50 mA max for 5 or 10 VDC supply. Normal Mode Rejection: Greater than 60 dB at 50/60 Hz Isolation: 4 kV input/output-to-power line. 500 V input-to-output or output-to-P+ supply. Overvoltage Category: Installation Overvoltage Category II: Local level with smaller transient overvoltages than Installation Overvoltage Category III. Environmental: Operating temperature range: -40 to 65°C Storage temperature range: -40 to 85°C Relative humidity: 0 to 90% non-condensing Connections: Removable screw terminal blocks accept 12 to 22 AWG wire, RJ45 for external relays, digital I/O, and serial communication adapters. Enclosure: 1/8 DIN, high impact plastic, UL 94V-0, color: black Mounting: 1/8 DIN panel cutout required: 3.622″ x 1.772″ (92 mm x 45 mm). Two panel mounting bracket assemblies are provided. Tightening Torque: Screw terminal connectors: 5 lb-in (0.56 Nm) Dimensions: 4.68″ x 2.45″ x 5.64″ (119 mm x 62 mm x 143 mm) (W x H x D) Weight: 9.5 oz (269 g) UL File Number: UL & C-UL Listed. E160849; 508 Industrial Control Equipment. Warranty: 3 years parts & labor USB Connection: Compatibility: USB 2.0 Standard, Compliant Connector Type: Micro-B receptacle Cable: USB A Male to Micro-B Cable Driver: Windows 98/SE, ME, 2000, Server 2003/2008, XP 32/64-Bit, Vista 32/64-Bit, Windows 7 32/64-Bit, Windows 10 32/64-Bit Power: USB Port
Inputs: Field selectable: 0-20, 4-20 mA, ±10 VDC (0-5, 1-5, 0-10 V), Modbus PV (Slave) Accuracy: ±0.03% of calibrated span ±1 count, square root & programmable exponent accuracy range: 10-100% of calibrated span Temperature Drift: 0.005% of calibrated span/°C max from 0 to 65°C ambient, 0.01% of calibrated span/°C max from -40 to 0°C ambient Signal Input Conditioning: Linear or round horizontal tank volume calculation. Multi-Point Linearization: 2 to 32 points for PV or PV1. 2 to 8 points for PV2 (Dual-Scale Level feature) Programmable Exponent: 1.0001 to 2.9999 Low-Flow Cutoff: 0-999999 (0 disables cutoff function) Decimal Point: Up to five decimal places or none: d.ddddd, dd.dddd, ddd.ddd, dddd.dd, ddddd.d, or dddddd. Calibration Range: 4-20 mA: minimum span input 1 & input 2: 0.15 mA. ±10 V: minimum span input 1 & 2: 0.10 V. An Error message will appear if input 1 and input 2 signals are too close together. Input Impedance: Voltage ranges: greater than 1 MΩ. Current ranges: 50 – 100 Ω (depending on resettable fuse impedance). Input Overload: Current input protected by resettable fuse, 30 VDC max. Fuse resets automatically after fault is removed. HART Transparency: Analog input will not interfere with existing HART communications on the wired 4-20 mA signal
Rating: 2 or 4 SPDT (Form C) internal and/or 4 SPST (Form A) external; rated 3 A @ 30 VDC and 125/250 VAC resistive load; 1/14 HP (≈ 50 watts) @ 125/250 VAC for inductive loads such as contactors, solenoids, etc. Noise Suppression: Noise suppression is recommended for each relay contact switching inductive loads. Deadband: 0-100% of span, user programmable High or Low Alarm: User may program any alarm for high or low trip point. Unused alarm LEDs and relays may be disabled (turned off). Relay Operation: Automatic (non-latching), latching (requires manual acknowledge), sampling (based on time), pump alternation control (2 to 8 relays), Off (disable unused relays and enable interlock feature, manual on/off control mode). Relay Reset: User selectable via front panel buttons or digital inputs. 1. Automatic reset only (non-latching), when input passes the reset point. 2. Automatic + manual reset at any time (non-latching). 3. Manual reset only, at any time (latching). 4. Manual reset only after alarm condition has cleared (latching). Note: Front panel button or digital input may be assigned to acknowledge relays programmed for manual reset. Time Delay: 0 to 999.9 seconds, on & off relay time delays. Programmable and independent for each relay. Fail-Safe Operation: Programmable and independent for each relay. Note: Relay coil is energized in non-alarm condition. In case of power failure, relay will go to alarm state.
Auto Initialization: When power is applied to the meter, relays will reflect the state of the input to the meter.
Protocol: Modbus® RTU (Slave Only) Meter Address/Slave ID: 1 – 247 Baud Rate: 300 – 19,200 bps Transmit Time Delay: Programmable between 0 and 199 ms or transmitter always on for RS-422 communicationv Data: 8 bit (1 start bit, 1 or 2 stop bits) Parity: Even, odd, or none with 1 or 2 stop bits Byte-to-Byte Timeout: 0.01 – 2.54 seconds Turn Around Delay: Less than 2 ms (fixed) Note: Refer to the ProVu Modbus Register Tables for details
Isolated 4-20 mA Transmitter Output
Output Source: Process variable (PV), max, min, set points 1-8, manual control setting, or Modbus input Scaling Range: 1.000 to 23.000 mA for any display range Calibration: Factory calibrated: 4.000 to 20.000 = 4-20 mA output Analog Output Programming: 23.000 mA maximum for all parameters:Overrange, underrange, max, min, and break Accuracy: ± 0.1% of span ± 0.004 mA Temperature Drift: 0.4 µA/°C max from 0 to 65°C ambient, 0.8 µA/°C max from -40 to 0°C ambient Note: Analog output drift is separate from input drift. Isolated Transmitter Power Supply: Terminals I+ & R: 24 VDC ± 10%. Isolated from the input at >500 V. May be used to power the 4-20 mA output or other devices. All skus rated @ 40 mA max.
35 VDC (external)
Digital I/O Expansion Module
Channels: 4 digital inputs & 4 digital outputs per module System: Up to 2 modules for a total of 8 inputs & 8 outputs Digital Input Logic: High: 3 to 5 VDC Low: 0 to 1.25 VDC Digital Output Logic: High: 3.1 to 3.3 VDC Low: 0 to 0.4 VDC Source Current: 10 mA maximum Sink Current: 1.5 mA minimum +5 V Terminal: To be used as pull-up for digital inputs only
4-Relay Expansion Module
Relays: (4) Form A (SPST) rated 3 A @ 30 VDC and 125/250 VAC resistive load; 1/14 HP (approx. 50 watts) @ 125/250 VAC for inductive loads
Signal Input Conditioning
Non-linear input signals can be linearized with the ProVu’s simple to use round horizontal tank linearizer or the ProVu’s powerful general purpose linearizer.
8-Point Linearizer for Volume
Round Horizontal Tank Signal Input Conditioner
For pump control applications where 2 or more similar pumps are used to control the level of a tank or a well, it is desirable to have the pumps operate alternately; this prevents excessive wear and overheating of one pump over the lack of use of the others. The ProVu can accommodate up to 8 pumps. In the example below, a pair of relays have been set up to alternate every time an on/off pump cycle is completed. Another pair of relays is used for low and high alarms.
Panel cutout required: 1.772″ x 3.622″ (45mm x 92mm)
Panel thickness: 0.040 – 0.250″ (1.0mm – 6.4mm)
Mounting brackets lock in place for easy mounting
Clearance: Allow 6″ (152 mm) behind the panel
MeterView® Pro Software
MeterView® Pro software is designed for use with ProVu, ProtEX-MAX, or Helios Series meters and allows users to remotely program, monitor, and datalog using a PC. Remote programming allows for all available meter settings to be programmed through an easy, user-friendly interface. The data acquisition feature allows the user to gather readings from a meter at user-selected intervals and generate charts using common tools like Microsoft® Excel. A linearization setup function is also included. With this utility the user can configure up to 32 linearization points and upload them to the meter. All configuration data can be saved to a file for future use. This software is accessible via the onboard USB connection on all Helios large display meters, ProVu panel meters, and ProVu-based ProtEX-MAX explosion-proof meters produced since 6 September 2016 (firmware version 4.0 or higher). In order for meters produced prior to 6 September 2016 (firmware version 3.1 or lower) to establish digital communications with a PC, a serial communications adapter is required. For an RS-232 connection, use a PDA1232adapter. To determine the software version of a meter:
Go to the Diagnostics menu () and press Enter button.
Press Up arrow button and scroll to Information menu (Info).
Press Enter to access the software number (), version (), and serial number () information. Write down the information as it is displayed. Continue pressing Enter until all the information is displayed.
The meter returns to Run Mode after displaying all the settings.